ARMY TM 9-6115-666-13&P
AIR FORCE TO 35C2-3-505-1
4.14. SWITCH BOX CIRCUIT BREAKER/SWITCH MAINTENANCE.
This task covers:
INITIAL SETUP :
Tool Kit, General Mechanic's
(item 1, appendix B)
Both generator sets shut down,
(item 2, appendix B)
Trailer support devices are lowered.
Switch box cover removed, paragraph 4.11.
Clear plastic panel covers removed,
The switch box contains four output circuit breakers and two input switches. Replacement
procedures are the same except the input switches have four screws and the output circuit
breakers have six screws.
1. Tag wires on circuit breaker(s) (2, figure 4-9) or switch (4) terminals and remove.
2. Remove six screws (1) securing the circuit breaker(s) (2) to the switch box or four screws (3) securing
the input switch (4).