ARMY TM 9-6115-666-13&P
AIR FORCE TO 35C2-3-505-1
SECTION III. MAINTENANCE PROCEDURES
Refer to TM 9-6115-645-24 for generator set maintenance, and to TM 9-2815-256-24 for engine maintenance.
Refer to TM 9-2330-376-14&P for trailer maintenance. Direct Support maintenance procedures are provided in
5.6. REPLACE GENERATOR SET.
This task covers:
INITIAL SETUP :
Tool Kit, General Mechanic's
(item 1, appendix B)
Both generator sets shut down, paragraph 2.7.1
Lifting device with a minimum 6000 lb. capacity
Trailer supports devices are lowered.
When lifting the generator set, use lifting equipment with a minimum lifting capacity of 6000
to swing. Failure to observe this warning can result in severe personal injury or death.
1. When removing the generator set from the power plant trailer, disconnect cable W1 or W2 (1, figure
5-3) depending on the generator to be removed. W1 is connected to generator set 1 and W2 is
2. Disconnect paralleling cable (2) from generator set paralleling connector.
3. Disconnect auxiliary fuel line (3) connected to generator set (4).
4. Disconnect ground cable from generator terminal (5).