ARMY TM 9-6115-666-13&P
AIR FORCE TO 35C2-3-505-1
Table 2-2. Operator Preventive Maintenance Checks and Services
for AN/MJQ-1612 andAN/MJQ-1632 (Continued)
Not Fully Mission Capable if:
Item to Check/Service
The fuels used in this generator set are highly explosive. DO NOT smoke
or use open flame when performing maintenance. Flames and explosion
can occur, resulting in severe personal injury or death.
Exercise extreme caution when performing "DURING" checks inside
engine compartment. Avoid contact with moving or hot engine parts.
Failure to observe this warning can result in severe personal injury or
GENERATOR SET -
Check for loose, damaged or
Inspect for leaks.
Any fuel leaks.
Class III leaks.
a. Inspect for leaks
Oil level below ADD level.
b. Check oil level on dipstick,
Listen for unusual noise in fan
Cable is missing or damaged.
Inspect ground rod and cable
for loose connections, breaks,
damage, and corrosion.
High voltage is produced when this generator set is operating. Improper operation
could result in injury or death.