ARMY TM 9-6115-666-13&P
AIR FORCE TO 35C2-3-505-1
2.3.4. Connecting Load Cables.
Never attempt to connect or disconnect load cables while the generator is running. Failure
to observe this warning could result in severe personal injury or death by electrocution.
Before connecting the load, determine voltage and frequency requirements of the system or
device that is being supplied with power. Refer to TM 9-61-15-645-10 and verify that
voltage reconnection board is in proper position for voltage requirements and the frequency
select switch is in the proper position. If board requires repositioning notify next higher level
220.127.116.11. Power Plant. Load can be connected to the switch box using any combination of connectors, J1
through J4, figure 2-6. The paralleling cable is already connected between the generators.
a. Remove load cables from the cable storage box located on trailer.
b. Connect the plug end of cable (1) to the desired connector of the switch box.
Figure 2-6. Connecting Load Cables.